Factory direct sales clean transfer window clean transfer window
The device must have a clean room auxiliary equipment, mainly for the clean area between clean area, clean area and clean area between the non-delivery of small items, open the door to reduce the number of clean room, clean room on the lower pollution levels.
1, the working area is made of stainless steel, flat and smooth, angles arc transition.
2, on both sides of the transfer window with a fan who started the functionality to make two in a door opening can be any automatic air.
3, UV germicidal lamp lighting and synchronized with the fans start to use.
4, users have special needs requirements, please specify when ordering.
|Clean level||Grade 100(209E U.S. Federal)|
|Dimension of working area(W1×D1×H1)||420*480*400mm||500*480*500mm|
Pass box is a kind of air purification equipment that used in the clean room.Clean type pass box is used for delivery small items between clean room and non clean areas.Using the pass box can effectively decrease the number of open the door for clean room,and reduce the pollution of the clean room to a minimum.
1. The working area is made of 304 stainless steel,the box body is made of 304 stainless steel,smooth and clean.
2. On both side of the door with electrical interlock device to realize interlock.When we use the machine,both sides of the door can not be open at the same time.
3. Electrical interlock device:Internal use of integrated circuit,electromagnetic locks,control panel,lamp and so on to achieve chain.When one door is opened,the switch indicator light of the other one is not bright,to inform that the door can not be open.At the same time,the electromagnetic action implementation chain lock.When the door is closed,the electromagnetic lock of the other door is starting to work,indicator lights up at the same time,the other door will open.There is a hole at the bottom of the control panel,the hole in the condition of the no electricity or emergency,with 1-3 mm wire sticking to the bottom,gently moves in the direction of the door can be directly open the door.
4. The complete set of the electric control is in the internal side of the pass box.If there are obstacles of the circuit can remove the inside of the plate for inspection or servicing.
5. Pass box is equipped with special sealing strip,to ensure the tightness according to different use increase indoor lights and germicidal lamp.